There are times when one feels that a stabilizer is not enough. After all, a stabilizer can correct voltage with a certain finite speed. We would think that our instruments are connected to a stabilizer and are unaware of the fact that it is stilt passing on the spikes, voltage surges, glitches, noise etc. Which are so short, that it cannot be corrected by a stabilizer.

What then? The answer is a C.V.T. from 'ASEEM-OORJA'^{®} This works on magnetic saturation principle, resonating with a tank circuit of high Q factor. When incoming Mains voltage is low the capacitor provides the necessary additional gain in power, keeping the output voltage steady. On the other hand , when the mains voltage is high the leakage reactance drops the difference of voltage. This correction of voltage is instantaneous even for sudden dips and spikes.

Capacities Available from 1.0 KVA to 10.0 KVA.
Ask for Custom Built CVT.

Features :

1. Proven technology

5. Rugged Industrial Design

2. High reliability

6. High efficiency

3. Fast response

7. CMRR & DMRR noise rejection up to 100 dB

4.
Output short circuit protected.

8. Can handle inductive loads

Technical
Specifications :

1. Input Voltage
Range

170 - 270 Volts A.
C. 1 ph.

2. Frequency

50 Hz + 2.5 Hz

3. O/P Voltage

230 V AC (
Adjustable to 220 V or 240 V )

4. Line Regulation

+ 2% at
rated load

5. Load
Regulation

1 %

6. Waveform

Sinusoidal

7. Response Time

20 ms.

8. CMRR Noise
Rejection

100 db.

9. DMRR Noise
Rejection

120 db.

10. Efficiency

Better Than 85 %

11. Total Galvanic
Isolation

5 KV

12. Energy Storage

3ms.

13.
Protection

a) Short CKT
b) Over Load
c) Fuse in the input CKT